Cite as [A.S.A.C. § 24.0720]
(a) Owners and operators must ensure that releases due to spilling or overfilling do not occur. The owner and operator must ensure that the volume available in the tank is greater than the volume of product to be transferred to the tank before the transferred is made and that the transfer operation is monitored constantly to prevent overfilling and spilling.
Note: The transfer procedures described in National Fire Protection Association Publication 385 may be used to comply with paragraph (a) of this section. Further Guidance on spill and overfill prevention appears in American Petroleum Institute Publication 1621, “Recommended Practice for Bulk Liquid Stock Control at Retail Outlets,” and National Fire Protection Association Standard 30, “Flammable and combustible Liquids Code.
(b) The owner and operator must report, investigate, and clean up any spills and overfills in accordance with 24.0750.History: Rule 3-01, eff 30 Aug 01.